Leaves Factory In 1-2 Days
Cummins Power Generation 20kW NG/LP Standby Generator Cold Weather Package with 200 Amp Automatic Service Entrance Rated Transfer Switch. Package also includes Remote In-Home Display and (2) 50 Ft. Installation Harnesses
EPA and CARB Emissions compliant models for California available upon request, no extra charge.
Comfort, Security and Convenience are the things you can depend on with a Cummins Residential Standby Generator...just in case the power goes out. With power outages occurring more and more frequently, it is good to be prepared. A Cummins Standby Generator can give you peace of mind and the ability to live your busy life, uninterrupted.
Generator Model 20GSBB-6714Features:
Very Quiet Operation
Internet remote monitoring and email notification, with the included In-Home Display
Load Management: Automatically turns on/off loads to prevent generator overload. Easy to set up from In-Home Display - INCLUDED. Easily connected at the generator.
Cummins designed alternator and electronic control
Powerful motor starting - starts and runs a 5 ton A/C under full pre-load
Self-diagnostic capability, Programmable Exerciser
Service and maintenance information displayed on the included In-Home Display
Easy installation with innovative molded polymer installation base - no need for a concrete pad.
Electronic Governor for precise frequency control
Flexible 12 inch fuel line provided with genset
Generator designed and manufactured in the USA.
Cold weather equipped with an engine oil heater and exhaust manifold intake heater for temperatures below 32 degrees.
U.S. EPA Emissions Certified
UL 2200 Listed and CSA Certified
5 Year, 2000 Hour Limited Manufactures Warranty
Transfer Switch Model RSS200-6869 Features:
200 Amp, Nema 3R (Outdoor Rated), Service Entrance Rated
Fully automatic control, selectable exercise at repeatable intervals.
Integrated, automatic 2 amp regulated battery charger.
Independent break-before-make action
Includes (2) 50 Ft Installation Harnesses:
p/n A029U302 Easy plug-n-play harness connects low voltage wiring between generator and transfer switch.
p/n A029U308 Easy plug-n-play connection from remote display to RS air-cooled generators. Color coded for easy installation.
|Manufacturer||Cummins Power Generation|
|Made In USA||Yes|
|Rated Amps||81 Amps|
|Voltage||120/240V Single Phase|
|A/C Ton Rating||5 Ton|
|Low Oil Alert||Yes|
|Battery Requirement||12V, Group 26R, 545 CCA|
|Mounting Pad||Composite Included|
|Product Weight||540 lbs|
|Shipping Weight||600 lbs|
|Dimensions (Inches)||53L x 43W x 34.7H||Engine|
|Engine Brand||Cummins Designed|
|Engine Size||993cc, OHV V-Twin|
|Cooling System||Air Cooled||Alternator|
|Auto Voltage Regulation||Yes||Fuel|
|NG Power Capacity||18kW|
|LP Power Capacity||20kW|
|NG Consumption @ Full Load||240 cu.ft/hr|
|NG Consumption @ 1/2 Load||135 cu.ft/hr|
|LP Consumption @ Full Load||3.0 gal/hr|
|LP Consumption @ 1/2 Load||1.5 gal/hr||Transfer Switch|
|Transfer Switch Model||RSS200-6869 Automatic|
|Transfer Switch Amps||200 Amps|
|Transfer Switch Circuits||Whole Service|
|ATS Poles||2 Pole||Warranty Information|
|Consumer Warranty||5 Year/2000 Hour Limited|
Posted by Paul on 17th Sep 2014
Looked at all others and decided to purchase this one. Costs more but well worth it. Quiet/well built/easy to install. Lost power within 4 hours of installing and this generator clicked on almost instantly. I could hear my neighbors generator noise over this one and I was standing next to it.
Posted by Unknown on 14th Aug 2013
Ordered from Norwall and was very pleased with customer service who provided advice throughout delivery and installation. The genset shipped very quickly, although actual delivery to the site was delayed by about a week due to the freight company's shuttling between a "hub" and "distribution center" and then back to the "hub" before they finally delivered.
Installed the genset myself and installed the transfer switch with the help of a licensed electrician (power company requirement). The installation went very smoothly and the integrated pad saved me time and money by not having to pour concrete. The electrician commented several times how impressed he was with the quality of the transfer switch and the entire setup.
The generator has functioned flawlessly during several power outages. It is so quiet that you may not know that it's in use unless you are outside near the genset or standing near the control panel.
I cannot comment about the web interface as there is no connection at this site.
Posted by Steve Hollander on 1st Aug 2013
I find this to be the most user friendly unit to install and program.
Posted by Steve Hollander on 1st Aug 2013
This is one of the finest generators on the market today for homeowners in the affordable range.
Posted by Mitch G on 27th Jun 2013
The generator is very quiet compared to others generators I have seen. It does the job it is intended to do. However the Ethernet port resets constantly causing the browser to not connect properly or lose connection while you are attempting to use the web interface. Sometimes you get weird looking pages et. The email setup is poor. For example the field “user name” is used for both logon and from email address. So if your server requires a login name that is different than the from address i.e. firstname.lastname@example.org the system will not work. Further it is plain smtp and not able to do any ssl or encryption on the net leaving the email ripe for hacking. Make sure you set up a special from email just for the generator. Also I am not happy with the way load shedding is designed. If I have 2 loads let’s say 2 Air Conditioner units on the load shedding if they both come on and usage is 95% it will shut both off and after 2 tries never turn them on again without manual intervention. It would be nice if you could have them cycle each load for a specific amount of time so one load would be on at a time as reasonably demanded.
I have heard there are issues with it and Windows 8 but I could not duplicate them
BTW I own one of the oldest microcomputer consulting firms in the USA
Posted by Joseph J. Z on 5th Feb 2013
After Sandy I knew we needed a backup in the event of another storm. I was surprised at the number of trees that had fallen and the big job that had to be done by LIPA. This generator was hooked up as directed by a licensed electrician and plumber and they were amazed as I on how quiet and smooth running the generator is. We have lost electricity only once since it has been hooked up. Did not hear anything until I opened the window and saw it working beautifully. I would recommend this generator to everyone for its reliability and craftsmanship.