Generac Guardian 10kW Standby Generator Pre-Packaged w/100 Amp-12 Circuit ATS
|We have kept the model's documents available for download:|
|Generac Preventative Maintenance Kit with 10W30 Oil for GT530cc 10kW HSB|
|Generac Preventative Maintenance Kit with 5W30 Oil for GT530cc 10kW HSB|
|Generac Oil Filter 070185D(B) 3 Pack|
|Generac Oil Filter 070185E 3 Pack Extended Life Oil Filter is 30% Longer, 30% More Capacity|
|Generac Preventative Maintenance Kit for 530cc Engines 2008-Current Models|
|Generac Oil Filter 070185D(B)|
|Generac Oil Filter 070185E Extended Life Oil Filter is 30% Longer, 30% More Capacity|
|Guardian Auxilary Transfer Switch Contact Kit|
|Guardian Bisque Paint Kit|
|Generac Oil Filter 070185D(B) 8 Pack|
|Generac Oil Filter 070185E 8 Pack Extended Life, Oil Filter is 30% Longer, 30% More Capacity|
|Generac Cold Weather Kit for Air Cooled 410 or 530cc Engines After April 2010|
|Generac Fascia Base Wrap for Guardian Air Cooled Generators 8-20kW Steel | 5839|
|Guardian Generator Transport Cart|
Generac Guardian Air Cooled 10kW Standby Generator Pre-Packaged w/100 Amp-12 Circuit Automatic Transfer Switch
Not only includes upgraded features with the Nexus controller but also includes several additional features.
• External common fault alarm: Allows for a connection to drive a common alarm if any shutdown for the generator occurs.
• Wiring Error: Gives indication if the transfer switch is connected incorrectly without allowing board damage.
• Battery Sentinal: Monitors battery to indicate that the battery is going to fail or if it has failed.
• Generator High Voltage Shutdown
• Internal Fault Shutdown: Shuts down generator in event of controller failure
• Nexus Controller: +/- 1% voltage regulation, smart charging battery system where output voltage is dependent upon ambient temperature and only charges the system when needed.
• External Mainline Circuit Breaker: Allows power shutdown without having to open or unlock the enclosure.
• Sturdy, galvanneal steel enclosure with RhinoCoat finish for superior weather protection.
• Digital NEXUS Controller, Two-line LCD Tri-lingual
• Product Activation: Requires each generator to be activated via website or phone before automatic function is enabled for warranty activation start point.
Includes: 100 Amp 12 Circuit Nema 1(Indoor Rated) Automatic Transfer Switch, Pre-Wired Conduits, Composite Mounting Pad, Flexible Fuel Line Connector, Pre-Wired External Connection Box
|Made In USA||Yes|
|Rated Watts||10 kW|
|Rated Amps||42 LP/37NG|
|Voltage||120/240V Single Phase|
|A/C Ton Rating||3 Tons|
|Decibel Rating||66 db(A)||Features|
|Low Oil Alert||Yes|
|Battery Requirement||Requires 12Volt-Group 26R-525CCA|
|Mounting Pad||Composite (Included)|
|Product Weight||387 lbs.|
|Shipping Weight||524 lbs.|
|Dimensions (Inches)||48 x 25 x 29||Engine|
|Engine Brand||Generac OHVI V-Twin|
|Engine Size||18HP/530 cc|
|Engine RPM||3600 RPM|
|Cast Iron Sleeve||Yes|
|Cooling System||Air Cooled||Alternator|
|Auto Voltage Regulation||Yes||Fuel|
|NG Power Capacity||9000|
|LP Power Capacity||10000|
|NG Consumption @ Full Load||156 cu.ft./hr.|
|NG Consumption @ 1/2 Load||102 cu.ft./hr.|
|LP Consumption @ Full Load||1.93 gal./hr.|
|LP Consumption @ 1/2 Load||1.25 gal./hr.||Transfer Switch|
|Transfer Switch Model||RTS12EZA1 Nema 1, Indoor rated|
|Transfer Switch Amps||100 Amps|
|Transfer Switch Circuits||12 Pre-Wired Circuits 5 - 15A 120V 3 - 20A 120V 1 - 30A 240V 1 - 40A 240V|
|ATS Poles||2 Pole||Warranty Information|
|Consumer Warranty||3 Years Limited|
|Commercial Warranty||3 Years Limited|
Posted by LP Schlosberg on 1st Oct 2013
I ordered my 10KW standby generator after Hurricane Sandy and was told that they were on back order. Delivery was sooner than expected but in the meantime I bought a 6KW portable gasoline generator locally. That got us power after Sandy but had to fill it with 6 gallons of gasoline and start it manually every day. When the cold weather was over, I had a cement slab poured for the Generac and was going to install it myself but finally found someone to install it at a reasonable price. After being hooked up to the gas line it started right up and starts every Sat. morning to do a self-check. After losing power during Irene and Sandy, it is nice to know that the power will come on automatically whether I'm home or not during the next power failure. I'm just sorry I didn't wait for the new model that is 11KW for the same price.
Posted by Charlie on 15th Apr 2013
We got the product after the storm. The installation and service from Phoenix Electric in Bridgewater, New Jersey could not have been better. Recommend without reservation.
Posted by A&J Electrical Inst., LLC on 8th Nov 2012
This item was purchased and installed for a customer with a 3k sf home. It ran for 8 days during Hurricane Sandy and they are more than pleased with it's performance.
Posted by RICK B. FROM OHIO on 21st Oct 2012
WE HAVE BEEN LOOKING INTO BUYING A GENERATOR FOR AWHILE AND AFTER LOOKING AT OTHER RETAILERS PRICES AND LOOKING AT NORWALLS IT WAS NO QUESTION WHERE TO PURCHASE OUR GENERATOR FROM. I ORDERED THE GENERAC 10K WITH NEXUS SMART SWITCH ONLINE WHEN NORWALL WAS OFFERING A FREE BATTERY,WHICH SAVED ME MORE MONEY ONTOP OF THE FREE SHIPPING,AND NO SALES TAX. THE PROCESS WAS FAST AND EASY,NORWALL SENT EMAIL CONFIRMING MY PURCHASE AND ALSO WHEN IT SHIPPED. I RECEAVED IT IN 7 DAYS AFTER PURCHASE AND IT ARRIVED PACKAGED ON A SKID IN EXCELLANT CONDITION AS PROMISED. I POURED A CONCRETE PAD AND PLACED THE GENERATOR ON IT, INSTALLING THE SMART SWITCH AND DOING ALL THE ELECTRIC HOOKUPS WAS NOT HARD IF YOUR FAMILIAR WITH DOING ELECTIC WORK. I DID HAVE MY PROPANE COMPANY COME AND RUN THE GAS LINE. THE GENERATOR WORKED GREAT AND PERFORMED THE EXERCISE CYCLE AS SCHEDULED, CAN'T WAIT FOR THE ELECTRIC TO GO OFF AND SEE HOW IT DOES.
Posted by E.Carey on 9th Oct 2012
We have purchased 5, 10K 100 amp generators for our new construction homes. We are always very pleased with Norwall's service and performance of our Generac generators. They cover the majority if not all the necessary backups we need. They give our clients the piece of mind needed during the worst outages.