Leaves Warehouse In 1-2 Days
Who is Generac?
Since 1959, Generac Power Systems has been designing and manufacturing backup power generators for residential, commercial and industrial applications. They have grown to be the world's largest provider of residential standby generators. Generac generators has revolutionized the commercial market with the first cost effective product line meeting the needs of small and mid-sized businesses.
The Generac Model 6237 generator provides standby power in an emergency. Installed with a Generac automatic transfer switch, it keeps your home supplied with power during a power outage, even if you are not home. The 6237 sold by Norwall Power Systems uses the state of the art Evolution Controller to handle all generator functions and ensure trouble free operation to keep the generator ready for use at all times. The Generac 8kW Guardian Generator comes with a 5 year limited consumer warranty.
Standby Generators from Generac operate on either LP gas or Natural Gas and are convertible in the field to accommodate either installation. The home's current fuel supply―either natural gas or LP gas―is usually the deciding factor when selecting the type of generator fuel. LP gas installations provide 8000 watts of capacity while natural gas provides 7000 watts. Fuel consumption at half load is about .87 gallons per hour for LP gas, and about 72 cubic feet per hour for natural gas. Fuel consumption is directly related to the electrical load and varies continuously during normal operation. Required fuel pressure to generator fuel inlet at all load ranges 3.5" - 7" water column for natural gas or 10" - 12" water column for LP gas.
The 410 cc air-cooled, overhead-cam industrial engine was designed and manufactured specifically for use in Generac's standby generators. It runs at 3600 RPM and is capable of producing up to 14.8 horsepower. Engine features include "Spiny-Lok" cast iron cylinder walls for extra rigidity and durability, a fully pressurized oil lubrication system, electronic ignition, and a 2 year / 200 hour oil change schedule for extended operation before maintenance is required.
The Evolution Controller by Generac operates the standby generator. When an outage occurs, it starts the generator and instructs the transfer switch to move the house onto generator power. During operation, it constantly monitors the load and engine speed to ensure consistent, utility grade power suitable for the most sensitive of electronics. At the same time, it monitors various sensors to ensure trouble-free operation.
Other features of the Evolution Controller include a programmable exercise period which keeps the generator lubricated and extends the life of seals and bearings. It includes a smart battery charger to keep the battery charged at its optimum level, a sophisticated fault detection system, and alerts the homeowner when maintenance is required. A dealer programmable start delay allows a 2 to 1500 second startup delay to prevent starting during momentary outages and voltage sags.
An optional wireless remote allows monitoring of the generator's status from inside the home. The advanced wireless remote allows you to remotely control generator functions, set maintenance alerts and exercise cycles, and test the generator. Mobile Link allows remote monitoring of generator status via web, email or texts.
The alternator generates electricity using a revolving magnetic field design which provides better voltage regulation and higher surge capacity than a stationary field. Combined with skewed stators on a stationary armature, the generator output is clean and steady even when the load is constantly changing. The high surge capacity allows the generator to start motors, even when other appliances have the generator under load.
The 6237 is 48 inches wide, 25 inches deep, and 29 inches high. With an eye pleasing design, an enclosure that resists corrosion, and a 62db noise level that is quieter than most central air conditioning units, this generator will fit well into any neighborhood. The unit cover opens to allow easy access for maintenance and locks with a key to prevent tampering.
Pre-wired 50 amp automatic transfer switch has a 30 foot whip to connect to the provided 5 foot pre-wired whip and external connection box. The pre-wired 2 foot whip, which is color coded, connects into the existing electrical panel. Rated Nema 1 (indoor installation only) has a total of 10 circuits in varying amperages. UL Listed.
|Manufacturer||Generac Power Systems|
|Made In USA||Yes|
|Rated Amps||33.3 LP/29 NG|
|Voltage||120/240V Single Phase|
|A/C Ton Rating||3 Ton|
|Decibel Rating||62 db(A)||Features|
|Low Oil Alert||Yes|
|Mainline Breaker||35 Amps|
|Battery Requirement||Group 26R, 12V, 525 CCA|
|Mounting Pad||Composite Base Attached|
|Product Weight||360 lbs.|
|Shipping Weight||473 lbs.|
|Dimensions (Inches)||48L x 25W x 29H||Engine|
|Engine Brand||Generac OHVI|
|Engine Size||410 cc|
|Cast Iron Sleeve||Yes|
|Cooling System||Air Cooled||Alternator|
|Auto Voltage Regulation||Yes||Fuel|
|NG Power Capacity||7kW|
|LP Power Capacity||8kW|
|NG Consumption @ Full Load||121 cu.ft/hr|
|NG Consumption @ 1/2 Load||78 cu.ft/hr|
|LP Consumption @ Full Load||1.42 gal/hr|
|LP Consumption @ 1/2 Load||.87 gal/hr||Transfer Switch|
|Transfer Switch Model||RTG10EZA1|
|Transfer Switch Amps||50 Amp - Nema 1 Indoor Rated|
|Transfer Switch Circuits||10 Pre Wired Circuits
1-30 Amp 240V
1-20 Amp 240V
3-20 Amp 120V
3-15 Amp 120V
|ATS Poles||2||Warranty Information|
|Consumer Warranty||5 Year Limited|
Previous | Showing reviews 11-14 of 14
Posted by Bill, New Jersey on 1st Sep 2013
Purchased this model# 6237 in July, 2013. Testing worked fine and I was going for a medical procedure early in the morning on August, 29. Went to bed early and the power went out at 11 pm for the first time for about an hour I didn't even notice until my wife told me.
I went out two more times that night. The unit worked perfectly. It was raining heavy and if I didn't have this unit I would have been out of bed three times hooking up my portable generator unit. This generator paid for itself in my opinion that night.
Posted by Ken P. on 29th Jul 2013
I bought a 6237 Generac 8kW in June. Order and delivery went very smooth. I installed it this weekend with help from Jim my brother in law. Norwall is the best and so is Generac, 7/27/13. I will tell all about my experience with both companies!
Posted by ken p. on 29th Jul 2013
Ordered Generac 6237 8kW from Norwall. Everything went very smooth from delivery to installation. Very happy I chose Norwall. Will tell all about dealing with Norwall and Generac. 5 stars all around.
Posted by Bill New Jersey on 19th Jul 2013
Ordered from Norwall in June and the item arrived as planned. The delivery man was very helpful. Model 6237 with free mobile link all hooked up works just as described, all I need in a power outage.
Previous | Showing reviews 11-14 of 14