Leaves Warehouse In 1-2 Days
Generac's most powerful GP Series portable generator supplies power at home and on construction sites. With features that offer ease of use, extended run time, safety and security, the 17500E provides up to 17.5 kilowatts of continuous power for everyday needs and a maximum of 26250 Watts of startup power for electric motors.
Emissions Certification: Not for sale in California, 49 State Only
Not for Sale in Canada
• Electric Start provides smooth, trouble-free engine cranking and starting.
• 6 AC receptacles including GFCI with circuit breakers. DC outlet for battery charging.
• 16 Gallon Fuel Tank provides up to 10 hours of runtime at 50 percent load.
• Pressurized Lubrication system with low-oil shutdown keeps critical parts lubricated.
• Idle Control saves fuel and reduces noise. Slower engine speed reduces costs, extends life.
• Hour Meter tracks use and provides alerts for timely maintenance.
• Lifting Eye Simplifies loading and unloading and provides security at job sites.
Receptacles are protected by circuit breakers to protect cords and prevent overloading. The 50-amp, 120/240 volt receptacle is protected by a toggle-type circuit breaker. All other AC receptacles have pushbutton-type breakers. The 12-Volt DC charging outlet is current limited to 10 amperes. 30-Amp and 50-Amp receptacles require the correct generator cables for use (sold separately).
• (2) 120V 20-Amp 5-20R Duplex receptacles (one GFCI) provide up to 2400 watts of power each.
• (2) 120V 30-Amp L5-30R Twist Lock receptacles provide up 3600 watts of power each.
• (1) 125/250V 30-Amp L14-30R Twist Lock receptacle for up to 7200 watts of power.
• (1) 125/250V 50-Amp 14-50R supplies 12,000 watts of power
• (1) 12-Volt, 10-Amp outlet allows battery charging using the included clip on battery cord.
This generator's ground is bonded to the frame for use as a portable. The floating neutral is not bonded to ground or to the generator frame to allow use with a two-pole manual transfer switch. Additional grounding lugs bonded to the frame allow connection to suitable earth grounds rods where required.
The 992cc OHVI engine was specifically designed for the demands placed on a portable generator engine. The fully pressurized lubrication system is similar to that used in automobiles and includes a spin-on automotive filter and automatic low-pressure shutdown to prevent engine damage. Oil is pumped directly to critical engine parts including bearings and valve lifter rods to ensure full lubrication during and after startup.
Plasma filled moly rings and plateau honed cylinders reduce oil consumption, provide better heat dissipation, and extend engine life.
The fuel system features a fuel-line shut off switch and pull-type choke. A push-button electric starter cranks the engine for smooth starts.
While under load, the engine operates at 3600 RPM. With the idle-control switch is set to on, it slows to 2100 RPM when the load is removed.
The GP17500E is mounted on a 1 1/4-inch tubular steel frame with two wheels and handles for easy maneuvering and placement. The output control panel, mounted under the handlebars, provides easy access to circuit breakers and receptacles. The durable resin fuel tank sits on top of the unit for easy access and fueling. Unit weight is 390 pounds.
Shipped with a 2-year limited consumer warranty or a 1-year limited commercial warranty.
|Manufacturer||Generac Power Systems|
|Made In USA||Yes|
|Voltage||120/240V Single Phase|
|Low Oil Alert||Low Pressure|
|Idle Control||No Load Low Speed|
|Receptacles||1 – 10 Amp 12V DC Battery Charger Input
1 – 20 Amp 120V 5-20R GFCI Duplex
1 – 20 Amp 120V 5-20 Duplex
2 – 30 Amp L5-30 Twistlock
1 - 30 Amp L14-30 Twistlock
1 - 50 Amp 14-50
|Product Weight||390 lbs.|
|Shipping Weight||513 lbs.|
|Dimensions (Inches)||48.5L x 30.75W x 38.50H||Engine|
|Engine Brand||Generac OHVI|
|Engine Size||992 cc|
|Engine RPM||3600 RPM|
|Fuel Tank Material||Resin|
|Fuel Tank Size||16 Gallons|
|Run Time (50% Load)||10 Hours||Warranty Information|
|Consumer Warranty||2 Years Limited|
|Commercial Warranty||1 Year Limited|
Posted by QuickieC on 14th Sep 2013
I purchased this generator from Norwall a while ago, very satisfied with this Generac generator. An electrician friend of mine installed the transfer switch. I have the battery hooked up to a trickle charge when not in use. This machine was a life saver for me during TS Irene & Superstorm Sandy. You can't go wrong with portable generator.
Posted by Ron Kelderman on 13th Dec 2012
If you would like to see my video review of this generator please go to You Tube and type in
ronkpaws1 or click on the link below.
Posted by John E on 11th Sep 2012
I recieved the GP17,500E in a very timely manor along with the delivery driver could not be more helpful. I found putting it together was very easy. When I tried the generator out, it started up with no problem and everything worked the way it was supposed to. I highly recommend this generator to others.I did replace my electric panel so I could have a transfer switch built in to the electric panel. Thanks for the fast delivery and the communications I recieved from Norwall power systems keeping me informed with the shipping information.
Posted by Ron K, Lexington, SC. on 23rd Jul 2012
This generac generator was shipped to me in a very timely manner. I was very satisfied to see that it was shipped on a heavy duty pallet. R/L Carriers also did a great job of delivering the generator to my home/ shop. The way that the frame is put together with rounded corners on the bottom helped me to be able to put the axles and wheels on without killing myself lifting one side at a time to put a floor jack under it and raise it high enough to put it all together. The reason I gave it 4 stars instead of 5 stars is because of only two miner problems that I found. One was the Positive battery cable from the battery to the starter rubs against the center vertical frame rail. I had to put a rubber guard around the cable with zip ties to protect it from grounding out against the frame if it rubbed through in the future. The second problem was the way that the gas line from the tank to the motor was routed. It goes at a angle downward coming out of the tank and then it goes up over a center rail and back down to the motor. I will drill a hole in the cross rail and install a rubber grommet so the fuel line will have a straighter path from the tank to the motor. Other than that it is very well made. I only had to put oil in the motor, put gas in the tank, and hook up the battery. It did not take but a few seconds to start up the first time. I ran it for awhile in both modes and it worked just like it was made to do. I ran some of my power tools to see how it managed the different loads and I found no other problems. I always look to buy things made in the USA and this is far and beyond better than foreign made junk and if I need parts in the future there is a dealer not to far from where I live. If this generator is the size you need I highly recommend it.